Frequently Asked Questions
AntrumX facilitates real-time demand control ventilation, allowing building managers to re-write the min. and max. ventilation rate each time a room’s air is sampled. AntrumX also allows laboratories and other critical environments to optimize ventilation by reducing air change rates when the space is clean.
The recommended sensor calibration interval is based upon application and ranges from 6 months to 5 years.
Antrum offers a 60-month product warranty due to a defect in material or workmanship resulting from normal use.
It is unlikely that a faceplate will become clogged with particles. However, AntrumEYE monitoring software sends a notification when air is not being sampled from a given room/space, prompting facilities personnel to examine the faceplate.
Use the number of thermostats in the space to determine the number of required faceplates. In a laboratory application it is recommended to sense in the general exhaust with a duct probe, and you should have one duct probe per 1,000 square feet.
The distance limit is 300 feet.
The distance limit is 100 feet.
The distance limit is 50 feet.
A minimum of 0.5″ of supply duct static pressure is required.
It is not mandatory for commercial installations, but highly recommended if available. In a laboratory application it is required, so that any air sample from the lab is exhausted out of the building.
In the main header, upstream of any VAV boxes or branch ductwork.
AntrumEYE is available on Android and iOS devices.